Henan mau duct rubber compensator by rubber and fabric composite material limit, steel flanges, steel rods, it is mainly used for a variety of flexible connection between fan, air duct, its function is to shock absorption, noise reduction, displacement and sealing, medium resistance, easy installation, is a kind of very ideal environmental protection field shock absorption, noise reduction, the best accessories and smoke prevention and dust control.
1 、風道橡膠補償器具有良好的反復位移 ( 變化 ) 還原性，能在較小尺寸范圍內提供較大的多維方向補償，能較好的消除各種管道安裝連接時產 生的多向誤差。
1, the air channel rubber compensator has good repeated displacement (change) reducibility, which can provide large multidimensional directional compensation in the smaller size range, and it can eliminate the multi-directional error produced by all kinds of pipeline installation and connection.
2. The air duct rubber compensator has the superior sound absorption and isolation function, and can effectively reduce and eliminate the transmission of sound and vibration of the system products such as boiler and fan.
3. The weak transmission loss of rubber and fiber reduces the design procedure and does not need to add other auxiliary facilities.
4, rubber and fiber fabric and heat insulation materials have high heat resistance and corrosion resistance, never rust, reduce maintenance costs.
5. The rubber compensator of the air duct has excellent air tightness and flexibility, and it can ensure that the conveying medium has no leakage and restores the original shape after repeated displacement.
1 、安裝長度由用戶在設計中選定，訂貨時未注明者按 L=350mm 的供貨。
2 、表中重量按一般安裝長度 L=350mm 計算。
3 、風道橡膠補償器中間有支撐架，支撐架在安裝前應保持不脫，待螺栓上緊后將其全部打掉，以保證安裝合理，使其各項物理機械性能真正起到 作用。
A brief description of the installation of rubber compensator for air duct:
1, the length of the installation is selected by the user in the design, and the unmarked order is supplied by the L=350mm.
2. The weight in the table is calculated according to the general installation length of L=350mm.
3, the air channel rubber compensator has a support in the middle. The support rack should remain unchanged before installation. After the bolts are tightened up, they will be knocked out to ensure that the installation is reasonable, so that all physical and mechanical properties will really play a role.
The rubber material of the rubber compensator of the air channel can choose three kinds of natural rubber, three yuan ethylene propylene rubber and three silicone rubber. The three kinds of rubber temperature resistance is as follows: natural rubber is below 80 degrees, three yuan, ethylene propylene rubber is below 120 degrees, and silicone rubber is below 200 degrees.